Dimmer Switch Tripped Breaker
I recently made the 3 lights that I had in the basement into 10 can lights. I also added a dimmer switch to that, which made the GFI in the garage permanently tripped. Therefore the outlets outside do not work at all because there is only one breaker. What should I do?
By Don from Omaha, NE
November 12, 20090 found this helpful
I'm no expert, but it appears you have overloaded the circuit. I'd call an electrician to fix it. Sometimes we can't do everything ourselves.
Add your voice! Click below to comment. ThriftyFun is powered by your wisdom!
You are viewing the desktop version of this page: View Mobile Site
© 1997-2016 by Cumuli, Inc. All Rights Reserved. Published by ThriftyFun
generated on October 11, 2016 at 2:01:36 PM on 10.0.1.5 in 1 seconds. Use of this web site constitutes acceptance of ThriftyFun's Disclaimer
. If you have any problems or suggestions feel free to Contact Us